Welcome to the fault-codes section of this site. The following table or page contains the information required to help repair and diagnose the fault codes being shown on the boiler display. You may be guided through the fault finding sequence or steps, for rectifying your boiler with this fault code. Suggested repair solutions may be provided by a link to a repair page. NB Some fault codes are only applicable to a specific range of boilers only.
According to the installation and servicing instructions manual, “safety switch-off: Flame simulation”. Also according to other sources, “Incorrect Flame Detection Fault (Flame Detection Even Though The Gas Valve Is Off)”
Cause of F27
According to the installation and servicing instructions manual. there is moisture on the electronics, electronics (flame monitor) defective, gas solenoid valve leaking. According to vaillant the causes are as follows.
Damage On The Electrode Or The Ignition Lead
Moisture Present On The Electronics
Fault On The Spark Generator
Fault On The Main PCB
Disclaimer: Information on this website is provided for informational purpose therefore we cannot accept liability for subsequent problems. All repair tasks should be carried out by qualified trades people.
We may also receive commission payments when you are taken to external websites and complete purchases from third party sellers, once you leave our site, we cannot be held liable for your purchases.